Inertia and Grid Stability
20 Dec 19 by Mark Howitt
The UK Black-outs on 9th August 2019
As is well known, on Friday 9th August the electricity supplies from one wind farm (Hornsea One, 750MW) and one generator set of one gas-fired power station (Little Barford, Cambridgeshire) failed almost simultaneously at 16:54. There was then a cascade of further trips within Little Barford, taking out the entire power station (680MW). The total capacity loss was ~1,430MW at the beginning of the evening peak. While National Grid’s power was restored by 18:00, disruption continued throughout the evening on the transport networks. 16:54 is in Settlement Period 33; 18:00 is the end of Settlement Period 36.
Batteries and DSR on 9th August
Battery and Demand Side Response (DSR) advocates have claimed that they provided 560MW power within 5ms to 2 seconds, and had stabilised the grid if only further generation trips hadn’t happened – if only there had been more batteries, the country would have been OK. But these trips occurred because of that 5ms to 2 second delay, so batteries were not part of the solution.
While batteries and DSR offer many useful grid services, shortfalls in their ability to provide sufficient grid resilience include:
- Inadequate scale: typical battery and DSR installations are (even when aggregated) of the order of 1-20MW while the system need was 1.43GW;
- Inadequate duration: the outage was longer than the duration of most battery and DSR services;
- Battery state of charge: National Grid’s plans appear to assume that batteries are always kept fully charged, whereas in reality they are all cycling in charge-state according to their contracts and commercial optimisation;
- Battery and DSR activation times: even if perfectly available, the fact that batteries and DSR (and gas reciprocating engine plants) need to be activated actively imposes delays in response of a few seconds, during which delays the system fails, whereas inertial systems are an always-on response;
- DSR response times: DSR resources need to be polled, signal availability, and then receive and respond to an activation signal, which increases their response times still further.
What is really needed is real inertia. The true story of August 9th is that there is generally less inertia on the system (proportional to total generation) than there has been since the construction of the grid due to the retirement of fossil fuelled power stations. That day, inertia was low because wind generation was high. Had there been sufficient inertia, only one or two trips would have occurred, not a cascade of many. Storelectric’s CAES solutions provide twice the natural inertia of an equivalent-sized power station, and provide it 24/7.
|Disclaimer. This document represents the intentions of Storelectric Ltd at the time of writing, which may change for various reasons including (but not limited to) technical, strategic, political, financial and the wishes of partners or investors. Any person or organisation considering investing in Storelectric does so at their own risk and is responsible for undertaking their own due diligence.|
Login on register to comment
Engerati Explains: Prospective Fault Level Monitoring
A foundation for electrical utilities in the digital age
- Fuel cells advancing in Europe Energy Generation
- New tariff proposal could resolve a looming problem with grid expansion Customers
- Engerati Explains: Prospective Fault Level Monitoring Strategy
- Developing projects on weak and saturated grids Energy Generation
- Shell Foundation and Aceleron delivering clean and affordable off-grid energy in Africa Distributed Generation
- Improving network efficiency with Ericsson’s AI-powered Energy Infrastructure Operations Artificial Intelligence
Developing projects on weak and saturated grids
Mark Howitt, CTO and co-founding director of long-duration storage developer Storelectric, explains how storage can reduce grid connection costs
Shell Foundation and Aceleron delivering clean and affordable off-grid energy in Africa
Africa could leap-frog other societies in developing energy storage as a service, says Dr Amrit Chandan, CEO of Aceleron.
Fluence and Statkraft deliver first large scale energy storage project in Ireland
Paired with the Kilathmoy wind project, the 11MW battery will provide split-second grid reliability
Related supplier content
Network Tariffs and Taxation
How do network tariffs work in the EU? Do you understand the opportunities they provide to flexibility services and decentralised solutions? smartEn, the European business association for digital and
E-Book: Energy storage
Energy storage steps up to the plate
Engerati marketing opportunities
Engerati is dedicated to helping utilities better adopt new technology and facilitate the transition of mass digital disruption.